VFD - BASICS
A thorough understanding of how to match the VFD to the driven load is the key to a successful application. When applied properly, the variable frequency drive (VFD) is the most effective motor controller in the industry today. Modern VFDs are affordable and reliable, have flexibility of control, and offer significant electrical energy savings through greatly reduced electric bills. They are used in a wide variety of applications for various reasons. For example, they are the most effective energy savers in pump and fan applications; they enhance process operations, particularly where flow control is involved. VFDs provide soft-start capabilities, which decrease electrical stresses and line voltage sags associated with full voltage motor start-ups, especially when driving high-inertia loads. To obtain a clear understanding of the proper and most effective application of VFDs, you first should gain a working knowledge of VFD basic theory as well as a strong familiarity with practical know-how. Basic VFD theory
Applying a VFD to a specific application is no mystery when you understand the requirements of the load. Simply put, the VFD must have ample current capability for the motor so that the motor can produce the required torque for the load. You must remember that machine torque is independent of motor speed and that load horsepower increases linearly with rpm. VFD applications can be divided into the following individual load types. Constant torque loads. These loads represent 90% of all general industrial machines (other than pumps and fans). Examples of these load types include general machinery, hoists, conveyors, printing presses, positive displacement pumps, some mixers and extruders, reciprocating compressors, as well as rotary compressors. Constant horsepower loads. These loads are most often found in the machine-tool industry and center driven winder applications. Examples of constant horsepower loads include winders, core-driven reels, wheel grinders, large driller machines, lathes, planers, boring machines, and core extruders. Traditionally, these loads were considered DC drive applications only. With high-performance flux vector VFD's now available, many DC drive applications of this type can be now handled by VFDs. Variable torque loads. Variable torque loads are most often found in variable flow applications, such as fans and pumps. Examples of applications include fans, centrifugal blowers, centrifugal pumps, propeller pumps, turbine pumps, agitators, and axial compressors. VFDs offer the greatest opportunity for energy savings when driving these loads because horsepower varies as the cube of speed and torque varies as square of speed for these loads. For example, if the motor speed is reduced 20%, motor horsepower is reduced by a cubic relationship (.8 X .8 X .8), or 51%. As such, utilities often offer subsidies to customers investing in VFD technology for their applications. Many VFD manufactures have free software programs available for customers to calculate and document potential energy savings by using VFDs. Sizing VFDs for the load
How do you size a VFD drive for an application and feel confident it's going to work? First, you must understand the requirements of the load. It helps also if you understand the difference between horsepower and torque. As electrical people, we tend to think of loads in horsepower ratings instead of torque ratings. When was the last time you sized something based on torque? Thus, both torque and horsepower must be carefully examined. Torque. Torque is an applied force that tends to produce rotation and is measured in lb-ft or lb-in. All loads have a torque requirement that must be met by the motor. The purpose of the motor is to develop enough torque to meet the requirements of the load. Actually, torque can be thought of as "OOUMPH". The motor has to develop enough "OOUMPH" to get the load moving and keep it moving under all the conditions that may apply....
Please join StudyMode to read the full document