# BOILER

Powerful Essays
Topics: Control theory
INTERNATIONAL JOURNAL OF CIRCUITS, SYSTEMS AND SIGNAL PROCESSING

Simulation of Power Plant Superheater Using
Pavel Nevriva, Stepan Ozana, Martin Pies
Abstract — The paper deals with simulation of both dynamics and control of power plant superheaters by means of Simulink Sfunctions. Superheaters are heat exchangers that transfer energy from flue gas to superheated steam. A composition of superheater, its input and output pipelines, and fittings is called a superheater assembly.
Inertias of superheater assembly are often decisive for design of a steam temperature control system. Mathematical model of a superheater assemble is described by sets of nonlinear partial differential equations. To analyze accuracy of the mathematical model, the system was agitated by test signals. Experiments carried out at the power plant were simulated mathematically. Data obtained by the measurement was compared with simulation results.

in [1]. Mathematical model of a pipeline or a header can be developed from the mathematical model of the heat exchanger by introducing zero heat transfer coefficient from the surrounding (making the pipeline isolated). The models comprise many coefficients. Coefficients of pipelines and headers are usually known with the relatively good accuracy.
Let us consider the mathematical model of the superheater assembly comprising superheater, its associated pipelines and pipe fittings. The accuracy of the model would depend on both the accuracy and correctness of coefficients of the model of the superheater. In this paper, the deterministic verification of the mathematical model of the superheater and its associated parts is presented. The verification process was as follows.
The superheater assembly of operating 200 MW power plant was agitated by the set of long term forced input signals. The dynamic responses were both measured and simulated. The measured and calculated results were compared.

References: steady states according the measurements Issue 1, Volume 5, 2011 IHI, Steam Generators, Technical Note of Ishikawajima-Harima Heavy Industries Japan, 2004. Cook R. D. at al., Applications of Finite Element Analysis, John Wiley and Sons, 2002, ISBN 0-471-350605-0 Haberman R., Applied Partial Differential Equations with Fourier Series and Boundary Value Problems, 4th Edition, Pearson Books, 2003, Jaluria Y., Torreance K.E., Computational Heat Transfer. Taylor and Francis, New York, 2003 ISBN 1-56932-477-5 Chen Chi-Tsong, System and Signal Analysis, Second Edition, Sundere College Publishing, 1989

## You May Also Find These Documents Helpful

• Powerful Essays

## Boiler

• 34436 Words
• 138 Pages

DISTRIBUTION SYSTEM Super High Pressure (SHP) Steam High Pressure (HP) Steam Medium Pressure Desuperheated (MPD) Steam Medium Pressure Desuperheated (MPD) Steam Low Pressure (LP) Steam Low Pressure Desuperheated (LPD) Steam Letdown Stations Steam Boilers Power Generation System Blowdown and Flash Drums CONDENSATE TREATMENT AND RECOVERY SYSTEMS Deaerators PCC NCC MP Condensate HP Condensate Condensate Treatment DESALINATED WATER…

• 34436 Words
• 138 Pages
Powerful Essays
• Satisfactory Essays

Boiler Manufacturer in China-ZG Boiler ZG Boiler is a China based boiler manufacturer company situated in Henan Province. We manufacture boilers, install and service a big range such as Gas Boilers, Steam Boilers, Fire Tube Boilers, Water Tube Boilers, Wood Fired Boilers, Package Boilers, D type boilers in Australia and other countries and areas and across the international market. Fire Tube Boilers Our fire tube boilers are manufactured to last, they are available in a variety of different designs…

• 413 Words
• 2 Pages
Satisfactory Essays
• Better Essays

cocks, valves and other fittings used for indicating water level are clear and are in good working order. Methods used to ensure boiler is in working order. Before a new boiler is initially fired, it should be given a complete and thorough inspection on both the fire side and water side. [pic] [pic] [pic] [pic] External examination of the boiler should include the visual inspection of the outer surfaces during operation as stated earlier. Other external points that should…

• 4041 Words
• 17 Pages
Better Essays
• Better Essays

Aim: To study the construction and working of various boiler mountings and accessories. Theory: A boiler is defined as a closed vessel in which steam is produced from water by combustion of fuel. Also defined as “A combination of apparatus for producing, furnishing, or recovering heat together with the apparatus for transporting the heat so made available to the fluid being heated and vaporized.” Classification of Boilers : The boilers may be classified according to following criteria: 1.…

• 1122 Words
• 5 Pages
Better Essays
• Powerful Essays

Boiler Basics Design and operation A boiler is an enclosed vessel that provides a means for combustion heat to be transferred into water until it becomes heated water or steam. The hot water or steam under pressure is then usable for transferring the heat for the steam requirements of process industries or for power generation. Combustion boilers are designed to use the chemical energy in fuel to raise the energy content of water so that it can be used for heating and power applications. Many fossil…

• 2571 Words
• 11 Pages
Powerful Essays
• Good Essays

BOILER OPERATION. Description of boiler operation SOFTENER: Function of softener is softening the hard water. This is because water supplied is hard water since it contains a lot of calcium, magnesium or other minerals. Water hardness Mg/L Soft water ≤ 17.1 mg/L Grey zone between soft and slightly hard water 17.1-60 mg/L Moderately hard 60-120 mg/L hard water 120 - 180 mg/L Very hard water ≥180 mg/L Hard water causes two problems such as 1. Dissolved calcium and magnesium…

• 798 Words
• 4 Pages
Good Essays
• Better Essays

ABSTRACT This experiment was carried out to determine the relationship between the pressure and the temperature of saturated steam in equilibrium. Besides that this experiment was also done to demonstrate the vapor pressure curve. The marcet Boiler was used for this experiment. When the pressure increases, the temperature also increases. Therefore, the relationship of pressure and temperature is directly proportional. The derived formulae and the data were used to calculate the slope. The dT/dP…

• 2252 Words
• 10 Pages
Better Essays
• Better Essays

Boiler Water Tests A BRIEF DESCRIPTION OF THEIR MEANING AND PURPOSE Expression of Test Results - PPM (parts per million) In water treatment, results are most commonly expressed in parts per million (ppm). Other terms commonly encountered are milligrams per liter (mg/l) and grains per gallon (gpg). For practical purposes, 1 ppm = 1 mg/l and 1 gpg = 17.1 ppm. The term “ppm” is unitless; that is, as long as the same units are used on both sides of the relationship, any units can be used. For example…

• 1581 Words
• 7 Pages
Better Essays
• Satisfactory Essays

Marcet Boiler 1. Abstract This experiment was carried out to determine the relationship between the pressure andthe temperature of saturated steam in equilibrium. Besides that this experiment was alsodone to demonstrate the vapor pressure curve. The market Boiler was used for thisexperiment. When the pressure increases, the temperature also increases. Therefore, therelationship of pressure and temperature is directly proportional. The derived formulaeand the data were used to calculate the…

• 372 Words
• 2 Pages
Satisfactory Essays
• Powerful Essays

the molecules become easier leaving the water surface while less energy required in achieving the state of equilibrium (boiling point). The temperature where equilibrium occurs at a given pressure level is called saturated temperature. The Marcet Boiler is used to investigate the relationship between the pressure and temperature of saturated steam in equilibrium with water at all temperature levels between the atmospheric pressure and 8 bars. The experimental slope (dT/dP)SAT obtained is compared…

• 1209 Words
• 5 Pages
Powerful Essays